CapT2 wall stations for the E-Flex Lighting
and Energy control system provide a capacitive touch button interface in a
Decora frame. Stations are connected using Cat5 cable.
CapT2 wall stations include button layouts with up to 7-buttons for simple ON/OFF to a 4-preset recall with OFF, and raise/lower control. The standard 4-preset recall layout is bank selectable via a dip switch on the rear of the station and can be configured to recall presets 1-4, 5-8, 9-12, or 13-16 from an E-Flex relay panel or E-Flex room controller.
By default a single zone is assigned to the corresponding CapX signal inputs on the EFRP (4 inputs) or EFRC (3 inputs) for out of the box operation as a standalone controller. Zone assignment can be unique for each CapT2 wall station or the same zones can be assigned to more than one CapT2 wall station. With multiple zones assigned, a station can recall full lighting looks which are editable on the relay panel. The 16 presets available on the relay panel can be edited with the PC-based E-Flex EFRP configurator tool software or using the on-board user interface of the EFRP.
Along with custom button layouts and legends, button actions can be programmed for preset toggle, zone toggle, occupancy override, etc.